Unittype: Water supply pipe.
Sensors used: FlowMoniSpot.
Solution: Are your pipes leaking?
Method: The sensors probe is mounted on the supply cable/pipe.
Configurations: The included alarms are added automatically if you select the unit type "water pipe" when the unit is registered on ReCalc. No other configurations are needed.
- Leaks: The leak alarm works by monitoring whether the water consumption goes to zero at least once a day. We can detect leaks from about one drop per second, corresponding to four liters per day.
- Missing flow: If it's difficult to identify any flow in the pipe, you will be warned. Alarms are still raised if they are detected. Missing flow can be due to a sensor installation failure, or because the temperature of the water in the pipe is close to the temperature of the surrounding air, which makes the alarm less sensitive.
- Missing data: If there has been a data drop out (big enough to make the leak detection invalid) no (false) alarms will be generated, and you will be warned.